Cautions for using the fuel tank of Xianning generator set
In the current market, there are many types of generators, which have different uses and diverse types, and are widely used in various industries. The main types of generators are land-based diesel generators, marine diesel generators, and special diesel generators. Although they are all diesel generators, their fuel tank designs are very different, so they must be very note.
The storage location of the fuel tank must be safe to prevent fire. The fuel tank or oil barrel should be placed in a visible place, away from the diesel generator set properly, and strict smoking regulations are not allowed; if the user makes the fuel tank, Shenzhen generator rental should Note that the fuel tank of the spare diesel generator set is made of stainless steel or steel plate. Do not spray paint or galvanize the inside of the fuel tank, because they will chemically react with the diesel, produce impurities that may cause damage to the diesel generator set, and reduce the quality and cleanliness of the diesel. And combustion efficiency.
After the fuel tank is placed, the highest oil level cannot be 2.5 meters higher than the base of the diesel generator set. If the oil level of the large oil depot is higher than 2.5 meters, a daily fuel tank should be added between the large oil depot and the diesel generator set to ensure the pressure of direct oil delivery. Not more than 2.5 meters. Even when the diesel generator set is shut down, fuel is not allowed to flow into the diesel engine through the oil inlet line or injection line by means of gravity.
The resistance at the oil port must not exceed the value specified in the performance data sheet of all diesel generator sets when using a clean filter element. This resistance value is based on half of the fuel in the fuel tank; the fuel pipe end position of the fuel tank should be about 50MM higher than the bottom of the diesel generator's fuel tank to prevent sediment and water from being sucked into the fuel supply pipe.
The connection of the fuel return line should not cause shock waves in the fuel pipe of the diesel generator set; the fuel capacity in the fuel tank should ensure daily supply; the fuel tank supply and return area should be provided with perforated partitions to reduce the diesel generator set Heat exchange.
The above brief introduction on the use of generator tanks is hoped, this knowledge will help you!
What factors affect the price of generating units
Detailed explanation of the four major shutdown protection issues of generator sets
What are the uses of small diesel generators
Nine factors of high water temperature in the water tank of the generator set
- 68KW Volvo generator set
- What are the components and functions of diesel generators? 2019-12-19
- Can the three-phase generator wiring diagram lead to only one phase ?
- Start-up steps of automatic diesel generator2019-12-05
- What is the reason for the small diesel generators to emit black smoke?
- What is the reason for ` ` maintenance '' diesel generators not catching fire?
- Maintenance tips and cleaning points for generators2019-10-26
- Introduction to the structure and characteristics of silent diesel generators2019-10-16
- Diesel generator wire grounding and UPS matching instructions2019-09-24
- Summary of faults used by generator set manufacturers